Sample pages from our Reports. All reports are full color, downloadable or printed with a summery page
Electrical Safety Issues- found in a 60 year old home.
Thermal Imaging - offered with every home inspection and mandatory with moisture & mold inspections
Sewer Camera Inspection- Tree roots growing in the joints of the 6" crock pipe installed in the 50's
We are on Facebook and Instagram for more up to date information and photos, Thanks for Looking!!!
Many issues here, first picture is a breaker no longer produced due to the reputation of not tripping and causing house fires. second is a breaker panel without a main breaker/ shut off with copper and aluminum wires together in the same lug. third picture is an outlet in the basement, no ground connected and should be a GFCI. fourth is old cloth lined wires not to code anymore and last is a outlet in the kitchen with out a ground. Many of todays standards have changed since the time this home was built, The cost of upgrading this system is worth the peace of mind. Caution-Check your homes electric panel for the names Federal Pacific or Federal NOARK or Federal Stablock, If you see one of these We recommend contacting a Licensed electrician for further examination or upgrading your panel. They were produced and installed from the 60's through the 80"s
Attic Inspection - Make sure your inspector goes in the attic.
Crawlspace Inspections - Yes we enter all safe, accessible areas